Total floor area, for all individual dwelling units, exceeding 8,000 square feet.
Total floor area of its nondwelling unit portions exceeding the limits established in par. (e)
A political subdivision's ordinances, enacted to meet the standards established in par. (d)
and this paragraph, shall require an automatic fire sprinkler system or 2-hour fire resistance in every multifamily dwelling that is constructed by any of the following types of construction if the total floor area of the nondwelling unit portions in the multifamily dwelling exceeds the following:
Type 3 metal frame protected construction, 8,000 square feet.
Type 5B exterior masonry unprotected, 5,600 square feet.
Type 7 wood frame protected construction, 5,600 square feet.
Type 8 wood frame unprotected construction, 4,800 square feet.
In this subsection, “fire detection, prevention, and suppression devices" has the meaning given in sub. (4) (g) 2.
A person may perform inspections of fire detection, prevention, and suppression devices being installed during the construction or alteration of, or the addition to, public buildings and places of employment only if he or she has received certification as an inspector from the department.
The department shall promulgate rules establishing procedures and requirements for issuing certifications for purposes of par. (b)
. The department shall include in the rules a requirement that the person hold a valid certification from the national fire protection association qualifying him or her as a certified fire inspector I or that he or she hold a valid equivalent certification.
The department shall determine which certifications issued by other entities will qualify as valid equivalent certifications. Notwithstanding s. 227.10 (1)
, determinations under this subdivision shall not be promulgated as rules.
The department shall provide assistance to any nationwide or statewide organization that represents fire chiefs and that is engaged in providing training and certification opportunities for persons seeking to receive certification by the department under this subsection.
History: 1971 c. 185
; 1971 c. 228
; Stats. 1971 s. 101.14; 1973 c. 324
; 1975 c. 39
; 1977 c. 29
; 1979 c. 221
; 1981 c. 320
; 1983 a. 36
; 1983 a. 189
s. 329 (8)
; 1983 a. 295
; 1985 a. 29
; 1985 a. 135
s. 83 (3)
; 1987 a. 288
; 1989 a. 31
; 1991 a. 187
; 1993 a. 261
; 1995 a. 27
; 1997 a. 27
; 1999 a. 9
; 2003 a. 269
; 2005 a. 78
; 2007 a. 148
; 2011 a. 257
; 2013 a. 20
; 2015 a. 240
; 2017 a. 331
See s. 66.0119
for provision authorizing special inspection warrants.
See also chs. SPS 314
, Wis. adm. code.
Inspection of buildings for safety and fire prevention purposes under this section does not involve a quasi-judicial function within meaning of s. 895.43 (3) [now s. 893.80 (4)]. Coffey v. Milwaukee, 74 Wis. 2d 526
, 247 N.W.2d 132
Sub. (4m) (b) limits the authority of the department under s. 101.02 (15) and sub. (4) (a) only insofar as it mandates the department to require sprinkler systems in multifamily dwellings that exceed twenty units or the specified floor area. Sub. (4m) (b) plainly does not restrict the authority of the department under other statutory provisions to promulgate rules requiring fire protection devices in multifamily dwellings that have fewer dwelling units or a smaller floor area than that specified in the statute. Wisconsin Builders Association v. Department of Commerce, 2009 WI App 20
, 316 Wis. 2d 301
, 762 N.W.2d 845
Record keeping of fires. 101.141(1)(1)
Each city, village, and town fire department shall file a report for each fire that involves a building and that occurs within the boundaries of the city, village, or town with the U.S. fire administration for placement in the fire incident reporting system maintained by the U.S. fire administration. The report shall be filed within 60 days after the fire occurs.
Each report filed under sub. (1)
shall include all of the following information:
The purpose for which the building was used at the time of the fire.
If the building was used as a home, whether the building was a multifamily dwelling complex, a single-family dwelling, or a mixed-use building with one or more dwelling units.
The number of dwelling units in the building, if the building was a multifamily dwelling complex or a mixed-use building.
Whether the building had an automatic fire sprinkler system at the time of the fire and, if so, whether the system was operational.
Whether the building had a fire alarm system at the time of the fire and, if so, whether the system was operational.
An estimate of the amount of damages to the building as a result of the fire.
The number of human deaths due to the fire, if any.
The number of human injuries due to the fire, if any.
Any other relevant information concerning the building, as determined by the fire department.
The department may review, correct, and update any report filed by a fire department under this section.
History: 1975 c. 224
; 2007 a. 75
As used in this section:
“Residential building" means any public building which is used for sleeping or lodging purposes and includes any apartment house, rooming house, hotel, children's home, community-based residential facility or dormitory but does not include a hospital or nursing home.
“Sleeping area" means the area of the unit in which the bedrooms or sleeping rooms are located. Bedrooms or sleeping rooms separated by another use area such as a kitchen or living room are separate sleeping areas but bedrooms or sleeping rooms separated by a bathroom are not separate sleeping areas.
“Smoke detector" means a device which detects particles or products of combustion other than heat.
“Unit" means a residential building or that part of a residential building which is intended to be used as a home, residence or sleeping place by one person or by 2 or more persons maintaining a common household, to the exclusion of all others.
A smoke detector required under this section shall bear an Underwriters Laboratories, Inc., listing mark or similar mark from an independent product safety certification organization.
The owner of a residential building shall install any smoke detector required under this section according to the directions and specifications of the manufacturer of the smoke detector.
The owner of a residential building shall maintain any such smoke detector that is located in a common area of that residential building.
The occupant of a unit in a residential building shall maintain any smoke detector in that unit, except that if an occupant who is not an owner, or a state, county, city, village or town officer, agent or employee charged under statute or municipal ordinance with powers or duties involving inspection of real or personal property, gives written notice to the owner that a smoke detector in the unit is not functional the owner shall provide, within 5 days after receipt of that notice, any maintenance necessary to make that smoke detector functional.
The owner of a residential building the initial construction of which is commenced before, on or after May 23, 1978, shall install and maintain a functional smoke detector in the basement and at the head of any stairway on each floor level of the building and shall install a functional smoke detector either in each sleeping area of each unit or elsewhere in the unit within 6 feet of each sleeping area and not in a kitchen.
Whoever violates this section shall forfeit to the state not more than $50 for each day of violation.
Department inspection and orders.
The department may inspect all residential buildings, except the interior of private dwellings, as may be necessary to ensure compliance with this section. The department may inspect the interior of private dwellings at the request of the owner or renter as may be necessary to ensure compliance with this section. The department may issue orders as may be necessary to ensure compliance with this section.
Contractor regulation. 101.1472(1)(a)
“Construction work" means construction, renovation, improvements, remodeling, installations, alterations, repairs, or demolition activities.
“License" means a license, a permit, or a certificate of certification or registration.
The department may not promulgate or enforce any rule that requires that a person who is engaged, or who offers to be engaged, in a business to do construction work hold a license issued under this chapter or ch. 145
unless the rule relates to a license specifically required by this chapter or ch. 145
History: 2013 a. 20
Contractor notices. 101.148(1)(a)
“Consumer" means a person who enters into a written or oral contract with a contractor to construct or remodel a dwelling.
“Contractor" means a person who enters into a written or oral contract with a consumer to construct or remodel a dwelling.
Depositing the document or written notice in the U.S. mail or with a commercial delivery service, addressed to the applicable person.
Giving the document or written notice personally to the applicable person.
“Dwelling" means any premises or portion of a premises that is used as a home or a place of residence and that part of the lot or site on which the dwelling is situated that is devoted to residential use. “Dwelling" includes other existing structures on the immediate residential premises such as driveways, sidewalks, swimming pools, terraces, patios, fences, porches, garages, and basements.
“Remodel" means to alter or reconstruct a dwelling. “Remodel" does not include maintenance or repair work.
Notice required at time of contracting. 101.148(2)(a)
Before entering into a written contract to construct or remodel a dwelling, or, if the parties enter into an oral contract, as soon as reasonably possible, but before commencing any work to construct or remodel a dwelling, the contractor shall deliver to the consumer a copy of the brochure prepared under s. 895.07 (13)
and a notice worded substantially as follows:
NOTICE CONCERNING CONSTRUCTION DEFECTS
Wisconsin law contains important requirements you must follow before you may file a lawsuit for defective construction against the contractor who constructed your dwelling or completed your remodeling project or against a window or door supplier or manufacturer. Section 895.07 (2)
of the Wisconsin statutes requires you to deliver to the contractor a written notice of any construction conditions you allege are defective before you file your lawsuit, and you must provide your contractor or window or door supplier the opportunity to make an offer to repair or remedy the alleged construction defects. You are not obligated to accept any offer made by the contractor or window or door supplier. All parties are bound by applicable warranty provisions.
The notice required under par. (a)
shall be conspicuous and in writing and may be included within the contract between the contractor and the consumer.
History: 2005 a. 201
Carbon monoxide detectors. 101.149(1)(am)
“Carbon monoxide detector" means an electronic or battery-operated device or system that sounds an alarm when an unsafe level of carbon monoxide is in the air.
“Fuel-burning appliance” means a device that burns fossil fuel or carbon-based fuel and that produces carbon monoxide as a combustion by-product.
“Residential building" means a tourist rooming house, a bed and breakfast establishment, or any public building that is used for sleeping or lodging purposes. “Residential building" does not include a hospital or nursing home.
“Unit" means a part of a residential building that is occupied by one or more persons as a home, residence, or sleeping place.
Carbon monoxide detectors required.
Except as provided in sub. (5)
, the owner of a residential building shall provide carbon monoxide detectors at the locations specified in par. (ax)
as required under pars. (ag)
Carbon monoxide detectors shall be provided in units that contain a fuel-burning appliance.