The CBRF shall maintain the yard, any fences, sidewalks, driveways and parking areas of the CBRF in good repair and free of hazards.
The CBRF shall be structurally sound without visible evidence of structural failure or deterioration and shall be maintained in good repair.
The CBRF shall ensure that
each courtyard, yard or other area on the premises of the CBRF is drained or graded to divert water away from the building.
The CBRF shall maintain each building in good repair and free of hazards.
The CBRF shall maintain all electrical, mechanical, water supply, plumbing, fire protection and sewage disposal systems in a safe and functioning condition.
The CBRF shall keep all furnishings clean, safe, and maintained in good repair.
The CBRF shall maintain storage areas in a safe, dry and orderly condition.
(3) Toxic substances.
The CBRF shall ensure that cleaning compounds, polishes, insecticides and toxic substances are labeled and stored in a secure area.
(4) Pest control.
The CBRF shall implement safe, effective procedures for control and extermination of insects, rodents and vermin.
(5) Garbage and refuse.
The CBRF shall dispose of garbage and refuse. Garbage and refuse in inside areas shall be kept in leak-proof, non-absorbent closed containers. Garbage and refuse in outside areas shall be in closed containers.
DHS 83.45 History
History: CR 07-095
: cr. Register January 2009 No. 637
, eff. 4-1-09.
DHS 83.46 Building support systems. DHS 83.46(1)(a)(a)
A CBRF shall maintain comfortable and safe temperatures. The CBRF shall provide tempered air at all times to eliminate cold air drafts. The heating system shall be capable of maintaining temperatures of 74º F. in areas occupied by residents.
The use of portable space heaters is prohibited except for Underwriters Laboratories listed electric heating equipment that is listed for permanent attachment to the wall. Portable space heaters shall have an automatic thermostatic control and shall be physically attached to a wall.
The CBRF shall maintain the heating system in a safe and properly functioning condition. The CBRF shall ensure that a heating contractor or local utility company completes all of the following maintenance and makes available to the facility documentation of the maintenance performed:
The CBRF shall have a chimney inspected at intervals corresponding with the heating system service under subd. 1.
The CBRF may not use a fuel-fired heater on the premises of the CBRF unless the heater is properly vented to the outside.
Any wood burning stove or fireplace shall have a flue separate from the flue used by a gas or oil fired furnace or boiler. The entire installation shall meet the requirements in NFPA 211. The CBRF shall have the wood burning or fireplace flue cleaned as often as necessary, but at least 2 times during each heating season. The CBRF shall make available documentation of the maintenance performed.
Combustible materials shall not be placed within 3 feet of any furnace, boiler, water heater, fireplace or other similar equipment.
The CBRF shall enclose any other open flame combustible fuel-burning device within a one hour fire rated assembly when sharing a common floor with a habitable room. A direct-vent appliance is exempt from this requirement.
All rooms and areas shall be well ventilated. Ventilation is not required in a refrigerated storage room.
A CBRF may not have transoms, transfer grills or louvers in bedroom walls or doors opening directly to a corridor.
(3) Public water supply.
The CBRF shall use a public water supply when available. If a public water supply is not available, the CBRF shall have a well that is approved by the state department of natural resources. The CBRF shall have the well water tested at least annually by the state laboratory of hygiene or other laboratory approved under ch. NR 149
. The CBRF shall maintain documentation of annual testing results.
Installation and maintenance.
The CBRF shall be supplied with electrical service, wiring, outlets and fixtures, which shall be properly installed and maintained in good and safe working condition.
The electrical service shall be of the proper size to handle the connected load.
DHS 83.46(4)(c)1.1. `Fuses and circuit breakers.'
Tamper-proof fuses or circuit breakers not to exceed the ampere capacity of the smallest wire size in the circuit shall protect the branch circuits.
2. `Ground fault interruption.'
Ground fault interrupt protection shall be required for all outlets within 6 feet of a plumbing fixture, all outlets on the exterior of the CBRF and in the garage.
Minimum number of fixtures and outlets.
The CBRF shall have all of the following minimum number of fixtures and outlets:
1. `Light fixtures.'
Every resident bedroom, bathroom, kitchen or kitchenette, dining room, laundry room and furnace room shall contain at least one approved or listed ceiling or wall-type electric light fixture equipped with sufficient lamps or tubes to provide at least 5 foot candles at floor level at the center of room. Where more than one fixture is used or required, the additional fixture or fixtures shall be equally spaced as far as is practical. A switched outlet may be substituted for a ceiling or wall fixture in resident bedrooms and dining rooms.
2. `Minimum outlet ratios.'
Electric duplex outlet receptacles shall be provided as follows:
Living room, dining room and bedroom, one per 75 square feet of floor area with a minimum of 2.
Kitchen, one per 8 lineal feet or fraction thereof, of countertop and preparation area, including island-type areas. In addition, if a kitchen is used for dining purposes, one per 75 square feet of floor area. Separate outlets shall be provided for refrigerators.
Toilet rooms, one, which may be part of the wall fixture if 72 inches or less from the floor.
Electrical outlets shall be located to limit the use of extension cords. Extension cords shall not be used in lieu of permanent wiring.
Switches or equivalent devices for turning on at least one light in each room or passageway shall be located to conveniently control the lighting in the area.
Temporary and exposed wiring.
All temporary wiring and exposed wiring, whether in use or abandoned, shall be removed.
DHS 83.46 History
History: CR 07-095
: cr. Register January 2009 No. 637
, eff. 4-1-09; correction in (3) made under s. 13.92 (4) (b) 7.
, Stats., Register January 2009 No. 637
; correction in (3) made under s. 13.92 (4) (b) 7.
, Stats., Register July 2011 No. 667
DHS 83.47 Fire safety requirements. DHS 83.47(1)(a)(a)
If the time it takes for any resident to evacuate is more than 2 minutes and up to 4 minutes, with or without employee assistance, the CBRF shall have all of the following:
If a resident has an evacuation time of 4 or more minutes, with or without employee assistance, the CBRF shall have all of the following:
If a resident cannot be safely evacuated from their bedroom as determined by the CBRF's assessment, the CBRF shall instruct the resident to remain in the resident's bedroom and the CBRF shall meet all of the following requirements:
Notify the local fire department and identify the specific residents using point of rescue, and provide an up-to-date floor plan identifying where those resident rooms are located.
The CBRF shall have a written plan for responding to emergencies and disasters that is readily available to all employees. The plan shall specify the responsibilities of employees. The plan shall include all of the following:
Procedures for orderly evacuation or other department-approved response during an emergency or disaster. The plan shall include procedures for any resident who refuses to follow evacuation or emergency procedures.
The CBRF's preparation for and response to severe weather including tornado and flooding.
How meals and medications will be provided to residents at the emergency shelter.
The disaster plan shall have an exit diagram that shall be posted on each floor of the CBRF used by residents in a conspicuous place where it can be seen by the residents. The diagram shall identify the exit routes from the floor, including internal horizontal exits under par. (f)
when applicable, smoke compartments or a designated meeting place outside and away from the building when evacuation to the outside is the planned response to a fire alarm.
Emergency and disaster procedures.
Fire, tornado, flooding or other emergency or disaster procedures shall be clearly communicated to a new resident within 72 hours after admission.
Fire evacuation drills shall be conducted at least quarterly with both employees and residents. Drills shall be limited to the employees scheduled to work at that time. Documentation shall include the date and time of the drill and the CBRF's total evacuation time. The CBRF shall record residents having an evacuation time greater than the time allowed under s. DHS 83.35 (5)
and the type of assistance needed for evacuation. Fire evacuation drills may be announced in advance.
At least one fire evacuation drill shall be held annually that simulates the conditions during usual sleeping hours. Fire evacuation drills may be announced in advance. Drills shall be limited to the employees scheduled to work during the residents' normal sleeping hours.
Other evacuation drills.
Tornado, flooding, or other emergency or disaster evacuation drills shall be conducted at least semi-annually.
The CBRF shall have approval from the department before including horizontal evacuation in the emergency and disaster plan.
CBRFs using horizontal evacuation shall document the total evacuation time of the fire zone evacuated.
Use of area of refuge.
The local fire department shall be made aware of the areas of refuge, if any, and the potential number of residents who would use the areas of refuge. Evacuation procedures involving fire department personnel shall be conducted at the option of the fire department. CBRFs using areas of refuge shall comply with construction requirements under s. DHS 83.51
Posting of emergency phone numbers.
The phone numbers for emergency services shall be posted near phones used by CBRF employees.
(3) Fire inspection.
The CBRF shall arrange for an annual inspection by the local fire authority or certified fire inspector and shall retain fire inspection reports for 2 years.
At least one portable dry chemical fire extinguisher with a minimum 2A, 10-B-C rating shall be provided on each floor of the CBRF. All fire extinguishers shall be maintained in readily usable condition. Inspections of the fire extinguisher shall be done by a qualified professional one year after initial purchase and annually thereafter. Each fire extinguisher shall be provided with a tag documenting the date of inspection.
A fire extinguisher shall be mounted on a wall or a post or in an unlocked wall cabinet used exclusively for that purpose. Fire extinguishers shall be clearly visible. The route to the fire extinguisher shall be unobstructed and the top of the fire extinguisher shall not be over 5 feet high. The extinguisher shall not be tied down, locked in a cabinet or placed in a closet or on the floor. Fire extinguishers on upper floors shall be located at the top of each stairway. Extinguishers shall be located so the travel distance between extinguishers does not exceed 75 feet. The extinguisher on the kitchen floor level shall be mounted in or near the kitchen.
Each CBRF shall develop and implement a written policy on smoking. The policy shall designate areas where smoking is permitted, if any, and shall be clearly communicated to residents. Designated smoking areas shall be well ventilated or have an alternate means of eliminating smoke.
DHS 83.47 History
History: CR 07-095
: cr. Register January 2009 No. 637
, eff. 4-1-09; correction in (1) (a) 2., (b) 3. made under s. 13.92 (4) (b) 7., Stats., Register December 2011 No. 672.