Underground tanks that store fuel for stationary combustion engines and gas turbines shall comply with ss. ATCP 93.545
ATCP 93.320 Note
Sections ATCP 93.545
address seldom-used and temporarily out of service tanks; change in service to store a non-regulated substance; tank system closures; conditions indicating releases; tank system integrity assessments; tank system site assessments; and responding to leaks, spills, overfills and releases.
ATCP 93.320 History
History: CR 17-092: cr. Register October 2019 No. 766, eff. 11-1-19. ATCP 93.330
Converted tanks for the storage of flammable and combustible liquids. ATCP 93.330(1)(1)
This section applies to all converted tanks, whether new or existing.
General installation and use.
Converted tanks for the storage of flammable and combustible liquids shall be installed by a certified installer.
Low-pressure tanks and pressure vessels that are being converted to the storage of flammable or combustible liquids at atmospheric pressure shall meet the applicable tank storage requirements of this chapter, specific to the liquid stored.
Tank supports shall be capable of supporting a static load equal to at least 2 times the weight of the full tank. This capability shall be confirmed by engineering structural analysis, by field testing, or by reference to an approved design standard.
The cargo tank of a tank vehicle that is converted to a stationary tank for the storage of flammable or combustible liquids shall meet the applicable tank storage requirements of this chapter, specific to the liquid stored, along with the requirements in pars. (b)
Cargo tanks for permanent stationary use shall be constructed of steel only.
The cargo tank vehicle platform shall be supported off the vehicle wheels and landing gear and secured against movement, by the use of blocking devices and anchoring mechanisms that are acceptable to the department.
Venting of the cargo tank shall follow the requirements of either NFPA 385 chapter 5 or this chapter.
(5) General administrative requirements.
Converted tanks shall follow the operating requirements of this chapter applicable to their current use.
ATCP 93.330 History
History: CR 17-092: cr. Register October 2019 No. 766, eff. 11-1-19; correction in (3) (b) made under s. 35.17, Stats., Register October 2019 No. 766. ATCP 93.335
Manufacture of organic coatings. ATCP 93.335(1)(1)
This section applies to storage tank systems for flammable or combustible liquids used in the manufacture of organic coatings.
The tank systems shall comply with NFPA 35.
A certified installer shall perform or supervise the installation.
Tanks existing by November 1, 2019, shall comply with the registration requirements in s. ATCP 93.140
by November 1, 2020, and shall comply with the spill and overfill requirements in s. ATCP 93.410
and with the transfer containment requirements in s. ATCP 93.420 (5)
by December 31, 2024.
ATCP 93.335 History
History: CR 17-092: cr. Register October 2019 No. 766, eff. 11-1-19; correction in (4) made under s. 13.92 (4) (b) 14., Stats., Register October 2019 No. 766. ATCP 93.340(1)(1)
Clearances at bulk plants that were in existence on may 1, 1991.
Bulk plant facilities that were in existence on May 1, 1991, with setbacks less than those specified in NFPA 30 section 22.4 may be renovated or updated, but no additional storage capacity may be added in violation of the specified clearances.
Standard color code.
All new and existing tanks and piping at bulk plants and terminals shall use the identification scheme in API 1637.
ATCP 93.340 Note
See s. ATCP 93.230 (11)
for color coding of fill pipe caps and manhole covers for underground tanks.
Type of identification.
The product identification scheme in API 1637 shall be accomplished by one of the following methods:
Location of identification.
Tags shall be permanently affixed to the valve at the unloading riser, the pump control valves, the valve of a storage tank and load rack and on the product pipe lines in at least 3 locations equally spaced between terminating points or valves.
Tank yards and diked areas shall be kept free from weeds, high grass, rubbish, and combustible materials that are not essential to the operation and shall be kept clean and orderly.
Security at bulk plants and terminal storage facilities.
Owners and operators shall be aware of regulations, standards and operating practices that relate to facility security.
ATCP 93.340 Note
Note: Information on how to develop a comprehensive site security program is available in the API document, Security Guidelines for the Petroleum Industry, or the American Chemistry Council document, Site Security Guidelines for the U.S. Chemical Industry.
Transfer operations at bulk plants and terminals.
In order to prevent a spill from moving beyond the loading or unloading area, any new or existing aboveground or underground storage tank which has a capacity of 5,000 gallons or more and which is drained or filled by pumping to or from a transport vehicle shall be provided with a catchment basin or treatment facility to contain the maximum capacity of the largest compartment of a tank car or tank vehicle loaded or unloaded at the facility. Existing tanks shall comply with this subsection within 2 years after November 1, 2019.
ATCP 93.340 Note
Federal Spill Prevention Control and Countermeasure requirements in 40 CFR 112
may apply to smaller product transfers. A catchment basin may consist of remote impounding.
Aboveground tanks at existing facilities.
Aboveground tank systems at existing bulk plants and terminals shall comply with subch. IV
Underground tanks at existing facilities.
Underground tank systems at existing bulk plants and terminals shall comply with subch. V
New bulk plants and terminals shall comply with PEI RP800; aboveground tank systems there shall also comply with s. ATCP 93.400 (3)
, and (7)
; and underground tank systems there shall also comply with subch. V
ATCP 93.340 History
History: CR 17-092: cr. Register October 2019 No. 766, eff. 11-1-19; correction in (6) (c) made under s. 35.17, Stats., Register October 2019 No. 766. ATCP 93.350(1)(a)1.1.
This section applies to tanks that store, handle, or use liquids which are federally regulated hazardous substances, in any concentration of 1 percent or more by volume, for the purpose of protecting the waters of the state from contamination.
ATCP 93.350 Note
The list of federally regulated hazardous substances covered in this subchapter, also known as the CERCLA List, is located in 40 CFR 302.4
, Table 302.4.
ATCP 93.350 Note
Other sections of this chapter regulate the storage and use of flammable and combustible liquids. Chapter SPS 314
— the Wisconsin Fire Prevention Code
, through the adoption of NFPA 1, Fire Code
also regulates the storage and use of liquids that have properties such as being flammable, combustible, toxic, water reactive, explosive, and corrosive.
ATCP 93.350 Note
See s. ATCP 93.140
for tank registration requirements and s. ATCP 93.145
for tank permit requirements.
Liquids within the scope of subd. 1.
that are flammable or combustible shall also meet the requirements of this chapter which apply to flammable or combustible liquids.
This section does not apply to any of the following:
Hazardous waste storage tanks that are licensed under s. 291.25
, Stats., except any tank containing a flammable or combustible mixture of hazardous wastes regulated under that section, and other liquids, is not exempt from this chapter.
Aboveground tanks which are used to store a federally regulated hazardous substance and which have a capacity of less than 5,000 gallons, and transfer operations involving these tanks, unless the substance is flammable or combustible.
Portable tanks containing liquids that are not flammable or combustible.
Design, construction and maintenance of tank systems for the storage of federally regulated hazardous substances shall be in accordance with good engineering practices and this chapter and shall be under the supervision of a qualified engineer.
The qualified engineer shall notify the department or authorized agent on form TR-WM-121 of an impending installation of a tank system under this section unless this notice is provided under s. ATCP 93.115 (2) (b) 3.
A written statement shall be provided that the system has been designed and will have construction oversight by a qualified engineer.
All new tanks and pipe systems shall have pressure or vacuum testing that shall assure that all components and connections are tight, in a manner equivalent to the protocol and parameters specified in NFPA 30 section 21.5 and PEI RP 100 sections 11 and 14, before the tanks and pipe systems are placed into service.
The qualified engineer responsible for design and oversight of construction of federally regulated hazardous substance liquid storage tank systems under this chapter shall meet the requirements of this paragraph.
The qualified engineer shall be competent in the engineering methods for designing and installing hazardous liquid tank systems.
The qualified engineer shall be a registered professional engineer, unless one of the exemptions in s. 443.14
, Stats., applies.
(3) General requirements for tanks.
Storage tanks shall meet all of the following requirements:
Tanks shall have a stable foundation under all operating conditions and be of sufficient structural strength to withstand normal handling and use.
Tanks shall be chemically compatible with the substance being stored.
Wear, vibration, shock, and corrosion.
Tanks shall be protected from failure due to internal and external wear, vibration, shock, and corrosion.
Fire, heat, vacuum, and pressure.
Tanks shall be protected from fire, heat, vacuum, and pressure that might cause tank failure.
Tanks that are subject to vehicle collision shall be protected from collision damage by vehicles and equipment.
If fiberglass-reinforced plastic material is used, the material shall be of sufficient density and strength to form a hard, impermeable shell that will not crack, wick, wear, soften, or separate under normal service conditions.
Tanks shall be designed, constructed and installed or certified by a qualified engineer in accordance with a standard recognized by the department that is developed by a nationally recognized association or independent testing laboratory.
Tanks used for underground storage shall be listed or shall be approved by the department.
Used tank systems that do not meet the standards for new tanks under par. (g)
or new piping under sub. (4)
may not be reinstalled for hazardous substance storage.
If a used tank meets the standards for new tanks under par. (g)
, it may be reinstalled provided it is certified by a qualified engineer for use.
Spill prevention at pumps and valves.
The owner or operator shall prevent spills and leaks at all pumps and valves that control a liquid hazardous substance by using one or more of the following methods:
Installation of seal-less pumps and valves, double-seal pumps and valves or equivalent technology.
Implementation of a pump and valve inspection, maintenance, and repair program that complies with subd. 2. b.
The frequency of inspection and scope of maintenance and repair shall be based on a minimum of 5 years of actual operating and service records, manufacturer's recommendation, or records for similar operations.
Installation of pumps and valves within a catchment basin, such as a drip pan, pad or secondary containment system, that complies with subd. 3. b.
The catchment basin shall be compatible with the substance stored for a period of time that will allow for cleanup under all operating conditions.
The catchment basin shall be inspected each day of operation for accumulation of liquid and shall have the capacity to contain all spills likely to accumulate in the basin.
Tanks subject to melting.
Aboveground storage tanks constructed of a material subject to melting when exposed to fire shall be located so that any spill or leak resulting from the failure of the material could not unduly expose persons, structures, or the environment.
Storage tanks subject to scouring by the inflow of materials, or subject to wear from manual gauging shall be equipped with wear plates, diffusers, or other means to prevent localized wear or corrosion.
If wear plates are used, they shall cover an area of at least one square foot and be installed in a manner that prevents crevice corrosion of the tank.